Gore Heating & AC believes in high quality cooling, heating and AC in Delco, NC at fair and reasonable prices.
for Delco, NC
Our Reviews by City
Responded to a no a/c call for a ClimateMaster geothermal split heat pump, found leaking evaporator coil and bad condensate pump. Turned unit off and left fan on to defrost coil and circulate air. Needs new coil or replace air handler.
Started up geothermal HVAC unit with a new Heil air handler, checked water pressures and added water to the system. Water in was 35 psi, water out at 31 psi. Temp in at 87.7, temp out ay 96.2. Checked other two units to ensure they were on and functioning properly. Called Mr Barnhart and let him know everything is functioning properly and he will need someone to adjust the thermostat.
Responded to a no a/c call on two geothermal split heat pump HVAC units. Downstairs left the GFI outlet was tripped so no power was getting to the condensate pump. Reset breaker, pump discharged water and unit came on. The upstairs unit had a bad capacitor, replaced capacitor and unit came on. Both units are functioning properly at this time