Gore Heating & AC believes in high quality cooling, heating and AC in Fayetteville, NC at fair and reasonable prices.
for Fayetteville, NC
Our Reviews by City
Baker - Fayetteville, NC
Friendly open service Tech's
Fitzgerald - Fayetteville, NC
Technicians were very friendly, professional, and took the time to listen to what I had to say and ask.
David - Fayetteville, NC
Johnathan was friendly, professional knowledgeable, and thorough and the cost was reasonable. I recommend using Gore Heating and A/C.
Repair of Oil Furnace
Morris - Fayetteville, NC
Excellent & Timely
Andrews - Fayetteville, NC
Problem happened on a Friday afternoon. Technician came in less than an hour, diagnosed, and fixed the problem quickly. His truck was well equipped, had the part needed, no "run for parts" was required. Excellent service.
Replaced defective gas log part
Honeywell - Fayetteville, NC
Jonathan arrived on time with proper tools and replacement part. I felt he was proficient to install the defective part. Clean up after himself, visit with our dog, complete required paperwork, then go on to his next appointment. Service was fine but the little replacement parts was nearly $300.00 [excessive].
great service technician
McCray - Fayetteville, NC
Debi gave us EXCELLENT CUSTOMER SERVICE, she was EXTREMELY KNOWLEDGEABLE ON GAS LOGS. Thanks again Debi for your expertise. The Harveys💑
Marsha - Fayetteville, NC
Richard is an accomplished Technician
Honeywell - Fayetteville, NC
Richard always provides the services we need with a smile and hearty laugh.
He Worked in the Rain
MJKH - Fayetteville, NC
They were determined to get my gas pack repaired ASAP; ordered part came in one day and technician worked in the rain to get the job done in the timeframe that was promised.
Great Service, Friendly, on Time.
Gagnon - Fayetteville, NC
Great service. Professional technician
Willie - Fayetteville, NC
Great experience. Very satisfied
I received great service. He was awesome.
Covington - Fayetteville, NC
Happy Its fixed
Lewis - Fayetteville, NC
Fixed my heater. Happy to have it working right.
Thanks for the check up and hope to hear more soon. A ten for the first visit. J Brisson
James - Fayetteville, NC
Great service, very informative when I asked questions
Joyce - Fayetteville, NC
Rick - Fayetteville, NC
Nic got in and got the job done quickly.
Great service as always!
Andrade - Fayetteville, NC
We have had this Company for years now and they are wonderful!!!
Hill, Raymond - Fayetteville, NC
Rich Hans was very friendly, professional and knowledgeable.
death by 1000 paper cuts
Wilson - Fayetteville, NC
The Duct work has been replaced and everything works - ultimately that is what we paid for and that is what we got - but getting there was very painful.Multiple no shows for school emergencies, bad weather, sick workers, and problems on other sites resulted in multiple no shows over a 10 day period. Of course - having to plan work, appointments, keeping the dogs inside, etc was made very difficult by this consistent unreliability.The work area was left in a shambles - pieces of insulation all over the yard, mud all over the deck of our house and driveway without even an offer to clean up.Deb did her best to keep us informed when she could but there seems to be a clear command and control issue here. We had a similar experience with Gore 2 years ago but thought we would give them another try given that they are familiar with the property and all. I am disappointed with that decision.
McCray - Fayetteville, NC
Mr. Richard Hans has been our service rep.. for some time We want to keep him always. He knows our house, system and problems we have had before with this 3 yr old system. Has always told the truth and understands where we come from.
Bowman - Fayetteville, NC
Odie - Fayetteville, NC
Gore Heating and A/C has serviced our 2 units for 11 years. Very pleased with the service they provide. Very knowledgeable technicians.
Baker - Fayetteville, NC
Kenny - Fayetteville, NC
Performed a platinum ESA Summer Maintenance. Cleaned coils, checked amp draws on motors and compressor. I found the 20x25x5 media filter was dirty and customer purchased the media filter I had on truck stop. Checked temperature split. Checked wiring, duct work. I checked 410A refrigerant pressures. Checked capacitor. The unit has a smell running in A/C mode and customer is going to talk to nick about options. The ceiling above Airhandler was leaking during last hurricane.
Summer PM. GP-7. No issues found.
Summer PM. GP-6. No issues found.
Hvac 4. Summer pm. No issues found.
Performed Gold ESA Summer Maintenance on GP-1. Checked unit with gold maintenance form. Unit is operating properly at this time.
Found unit improperly installed. Need remove system, install new equipment pad. Repair gas piping and install a drain line. Install additional return and make a new equipment shroud.
Performed platinum ESA preventive Maintenance. Found unit low on R22. Did leak search and found leaking evaporator coil. I went over cost of repair and replacing.
Upon arrival checked HVAC system and performed a Gold maintenance. Cleaned coils on outdoor condenser and found that the bearing in the condenser fan motor are losing oil and compressor is starting at 102.8A. Suggest replacing condenser fan motor and added a start assist device to the compressor. Also upon inspection found that the unit has a leaking evaporator coil and a bad condensate pump underneath. Customer would like repair vs replace options and will call and schedule an appointment to come to the office to go over the options.
Performed Gold ESA Summer Maintenance. Checked pressures, amp draws on motors and compressor. Checked and cleaned coils. Checked temperature split. Unit is operating properly at this time.
Performed a Silver ESA Summer Maintenance. I checked pressures, amp draws on motors and compressor. Checked capacitor MFD. inspected evaporator, and condenser coil. Checked filter, thermostat, and temperature split. Unit is operating properly at this time.
Performed Summer ESA Maintenance on HVAC-5 (Gym kitchen). Checked split system heat pump. No issues with condenser, but while checking Air handler I found a faulty drain pan safety switch. The switch needs to be replaced. Replaced float switch. Unit is operating properly at this time.
Performed Summer ESA Maintenance on HVAC-4 (Gym). Checked everything on maintenance form. Form is attached to email. Unit is operating properly at this time.
Performed silver ESS Maintenance. Unit unit is operating properly at this time. Customer is going to call tomorrow to renew agreement.
Performed ESA summer maintenance on Heil gas pack. Unit is operating properly at this time. Customer is ping to call tomorrow and renew Maintenance agreements.
Performed ESA Summer Maintenance on HVAC-1(Gym). Checked amp draws on motors and compressors, checked wiring. I found a leaking Schroeder valve on the number 1 compressor making it 2lbs low on 410A. Will add 410A. I added 2lbs of 410A. Checked pressures and operation. Unit is operating properly at this time. At the time of repair no one was available for a signature.
Diagnosed the common wire was not plugged into nest thermostat. Hooked common wire up. Checked operation and unit is operating properly at this time.
Sent quote for replacement of condenser fan motor on AC-3
Arrived at a no A/C call for AHU-9 which heats and cools kitchen. I found a low voltage wire that broke and rubbed against the cabinet causing the unit to trip the 5amp fuse in the airhandler. I replaced the fuse and checked units operation. Unit is operating properly at this time.
Clean indoor coil to allow further diagnosis.Cleaned indoor coil. Pressures still spiking in heat mode, dropping in ac mode. Exams entire return side, no obstructions found. I cleaned evaporator coil and condenser coil. I replaced the control board because it was not telling the unit to switch from heat mode to coil mode. I checked pressures and amp draws. Unit is operating properly at this time.
Installed water heater, made sure lines were ok and there were no leaks.
Quote for repairs
I performed a ESA Summer Maintenance on HVAC-3(Gym). Checked all wire connections, amp draws on motors and compressors, checked capacitors and 410A pressures. Unit is operating properly at this time.
I completed a gold summer maintenance on HVAC-2 (Gym). I checked all wiring, amp draws, and pressures. Unit is operating properly at this time.
New Gas Line, Needs 24" NG Logs and Hood
Performed summer pm on back porch gas pack. System operating properly at this time.